Interested in linking to "How to perform Solenoid testing "?
You may use the Headline, Deck, Byline and URL of this article on your Web site. To link to this article, select and copy the HTML code below and paste it on your own Web site.
QUESTION:I WANT to perform a life assessment calculation for a Solenoid valve to identify basically how many years remaining for it. This calculation shall be based on real environment condition that the solenoid is kept. Such real outside temperature like 55 DEG C in Summer. Humidity 100%. Also, I was advised to use the following to search via google about "Reliability, Maintainability and Risk" by David J.Smith, or else for "Weibull Analysis," but I can't narrow the search to find a typical calculation that is done any general instrument like control valve and so on. Can you help to focus my look at this?
I FIRST addressed this question in about 1980 when a Du Pont colleague was investigating reliability and safety shutdown systems. His work eventually led in to the effort in ISA SP84. My conclusion then, and I still believe this is valid, is that there is no way to accurately calculate or predict solenoid valve failure in the general sense.
Most failures I saw during my years on the plants (20) were electrical. Some of these were very interesting with whole sets of SVs failing at one time during a unit start up. Rare failures have been seen with dirt blocking either flow or, more likely, switching. Water frozen in air lines can prevent operation, I suspect this problem is very rare in Saudi Arabia! Dirt and water are enemies of reliable operation of any pneumatic systems.
Another sort of failure experienced was a failure to switch because the DC voltage applied was not quite sufficient to overcome the magnetic structure in the valve. Note that the required pull-in voltage is higher than the hold-in voltage. These different values might not be listed in the catalogue specifications. I have been a party to opening up valves and adjusting the internal magnetic spacing.
Electrical failures may be linked to voltage spikes, or the reverse, low voltage heating the coils but insufficient to cause armature motion which would reduce current to a lower value in AC applications. Exposure to voltage/current spikes is heavily dependent on installation practices and even local earth conductivity. Voltage suppressing diodes are sometimes used. These may raise questions of possible of their failure to a shorted condition. Long wire runs will increase exposure to lightning induced spikes. There is a large difference in coil temperature between valves normally energized and those normally deenergized. It is generally believed that heat contributes to coil failure. My conclusion was that some brands and model numbers seemed more likely to fail. I have no way to prove this, and would never name names.
One approach supported by SP84 is that proof of reliability can be achieved after extended experience in exactly the same service. This is not much help until enough service time has passed to develop useful data. Proper record keeping is required for this, but not often seen.
The only recommendations that I could make is to select valves from a proven reputable manufacturer, that they are used well within their ratings, and installed in a manner to reduce exposure to voltage spikes and excessive heat. If very high reliability is required, then redundancy in the system design is required to reduce the impact of any single failure. That being said, I reject some of the quoted valve failure numbers which make solenoid valves look terrible, this is not justified by experience. It all comes down to intelligent engineering of the entire system and application.
RESPONSE:I WOULD like to wish you happy new year, and also thank my teacher Dr. Liptak for his excellent support to give me this occasion to talk to an experienced person. In relation to your feedback, I have the following:
MY COLLEAGUES of process control professionals and myself are answering many more questions than the few, which get published in Control Magazine. These combinations of questions and answers you can find on our web page under “Ask the Experts” at www.ControlGlobal.com.
Thank you for describing Indian practices on solenoid valve (SOV in your letter) maintenance, life expectation and turn-around (T/A in your letter). I am sure that Cullen Langford will comment on them and inform you of or – industry specific - American practices. I also hope that Cullen will visit with you, so that you might benefit from his experience.
ControlGlobal.com is exclusively dedicated to the global process automation market. We report on developing industry trends, illustrate successful industry applications, and update the basic skills and knowledge base that provide the profession's foundation.