# Regulating inlet fluid temperature

## In this installment of Ask the Experts, Béla Lipták and his cadre of leading experts in process automation, share tips on regulating inlet fluid temperature and controlling the stroking time of a control valve.

1 of 2 < 1 | 2 View on one page

QUESTION: How do I regulate inlet fluid temperature for a solar water heater so that it will remain within +/- 1 °C from the temperature wanted? We have a outdoor test facility for solar collectors, and we want to test different sizes and models of collectors.

We want to input water into a collector in different temperatures, e.g., beginning from ambient temperature (20 °C), feeding the collector for, say, half an hour, then during a few minutes, change the temperature to 35 °C, keep it there for another 30 minutes, change it to 50 °C, etc.

We have a three-way valve with a regulator controlling the inlet temperature. One pipeline feeds it with cool water, and the other has an electric bypass heater. The heater cannot keep the water temperature fixed, but it fluctuates within a range of ±10 degrees.

I’ve planned to remove the heater and connect the other pipeline coming directly from the collector outlet. The other pipeline would still input cooled water. The whole system is closed, and includes a 200-liter tank with expansion unit.

The concern is that the outlet water temperature from the collector will not remain constant. This will set high demands for the valve and its controller to cope with the changing temperatures.

Does anyone know of any similar test facility? If so, does it work? Can you give me hints of another decent way to control the collector inlet temperature in a closed circuit?

Flow speed will remain constant during the test, although we want to test it with different flow rates. The minimum flow rate will be approximately 50 liters/hour and the maximum 600 liters/hour.

Petri Konttinen

The only chance of success is to use feed-forward control from temperature with feedback trim. If the three-way valve is perfect, i.e. the openings are perfectly linear with stem position and always add up to a constant Cv, the feed-forward model is simply

M = (Th – T)/(Th – Tc),

where M is valve position as a fraction of cold water to the total, Th and Tc are measured hot and cold water temperatures, respectively, and T is the set point of the blend. To add feedback, replace T in the equation with the output of the feedback temperature controller.

Any valve imperfection will lead to a feed-forward error and require action by the feedback controller. If the imperfection is systematic, the valve may be characterized to correct it. A digital positioner should be applied to the valve to eliminate dead band and other non-systematic errors. The dynamics of the feedback controller and any lead-lag feed-forward compensator may require scheduling as a function of total flow.

Greg Shinskey, Consultant

 FIGURE 1: PNEUMATIC DIAGRAM OF A CONTROL VALVE

QUESTION: The figure to the right (Figure 1) is the pneumatic diagram of a control valve installation. Is a booster recommended for controlling the stroking time of the valve? My experience is that if the bypass valve (RS in Figure) isn’t in a good position, the booster can cause the valve to hunt continuously. Is it possible that after the initial adjustment of the control valve during startup, because with time the trim wears or process conditions change, the valve will start to hunt and require readjustment? The pneumatic positioner is a Fisher 3560 V/P. The booster is a FAIRCHILD Model 20512-DN1/4.

Nicolae (NICU) Costoae

Large control valves and large actuators may require flow or pressure boosters installed between the positioner and the actuator to achieve the required speed of response without hunting. One special “dead-band booster” design is shown in Figure 2 below. It does not respond to an input signal change until an approximately 1 psi (6.9 kPa) difference is reached between input and output signals.

In this design, a built-in needle valve allows a limited airflow to bypass the booster gain portion of the relay and provides adjustable damping. In response to fast input signal changes, this booster provides large volume amplification, but it does not amplify a slow change.

One common application for this relay is in centrifugal compressor anti-surge controls, where the control valve must open very quickly (1 to 3 seconds), but after opening, it should throttle smoothly. The needle valve is adjusted when the complete control system has already been assembled and is in operation. Careful tuning is vital for proper operation. When the needle valve is fully closed and the loop is hunting, one should gradually open the valve until hunting stops.

Best operation occurs when the needle valve is open just enough to smoothly dampen the oscillations. If, in order to increase capacity, more than one of these relays is used in parallel, it is absolutely necessary to match the openings of the needle valves to avoid unstable interaction between the relays.

Béla Lipták

1 of 2 < 1 | 2 View on one page

# Join the discussion

Want to participate in the discussion?