By Monte Smith
United Canadian Malt Ltd. (UCML) is Canada's largest manufacturer of a wide variety of liquid and dry, diastatic and non-diastatic extracts of malted barley, wheat, oats and rice. Our company was founded in Peterborough, Ontario in 1929, and since then has been a major international supplier of premier malt extracts and sweeteners for the food, pharmaceutical and brewing industries. Our customer base is extremely diverse, as customers use our ingredients in everything from cereal, bread, biscuits and pastries to chocolate, pet food, vinegar, chewing gum, ice cream, and, of course, beer.
Malt extract is a vacuum-concentrated sweetener made from high-quality malted barley. United Canadian Malt manufactures approximately 300 different liquid extracts using a variety of grains and process parameters to produce these natural, viscous sweeteners. In the food industry, extracts are used in a variety of baked goods, as the fermentation process assistance improves structure, color and crust appearance. The additional advantage is malt extract's ability to enhance these foods naturally with a unique, subtle and desirable flavor.
UCML is a certified organic production facility offering liquid extracts and syrups made from a range of organically certified grains. In the pharmaceutical industry, the distinct flavor of both liquid and dried malt extracts is an effective vehicle for active substance administration. With its broad nourishment characteristics, malt offers an improvement over plain sugar syrups.
At our facility, the main ingredient, malted barley, is stored in two outdoor silos. From them, it is drawn, crushed and then blended with water to yield a slurry called "mash." Precise quality control on temperature, time and specific water quantity allows the release of nutritional components from the grain. During this process, the natural enzymes inherent in the malted barley convert the grain starches and proteins to soluble and digestible sweeteners and protein components. The resultant fluid, called "sweet wort," is separated by filtration from the spent grains. The wort is then concentrated by evaporation to produce a viscous malt extract consisting of 80% solids material.
Brewing production scheduling requires an accurate assessment of our primary ingredient—the malted barley, which is stored in UCML's two 15-m (49.2-ft) steel silos. To do so, we need a very reliable, accurate and robust system to provide constant grain level information from our silos.
Our previous weight and cable level measurement system and rotary paddle switches resulted in ongoing maintenance and reliability issues. Imagine removing caked-on grain dust from an inoperative spindle wheel atop a 15-m (49.2-ft) silo during a June rainstorm. Or better yet, reseating the control rope and winding motor in January's frigid and icy weather.
When the electronics of the weight and cable system failed, we temporarily used a manual level control system. Time and safety issues were substantial cost and efficiency factors, however, as workers had to climb the silo, open the hatch and check levels with a flashlight. And, really, just how accurate is that flashlight level check? Truthfully, the only benefit from all of this climbing to the top of the silos was the positive effect on the manager's heart rate and his fresh air exposure!
All of this took place at UCML with malted barley grain arriving by rail car or truck every few days. Grain delivery was always a control headache, as the silo's capacity is much less than the more than 70 metric tons (MT) on a rail car. With the variable delivery schedules and the expense of rail car unloading demurrage time, it is crucial to have constantly accurate inventory level measurement. Precise inventory monitoring ensures that unloading from rail cars or trucks takes place within the allotted days, and without exceeding the silos' capacity, since cleanup of spilled grain on surrounding streets is not easy. We also wanted the ability to coordinate the brewing usage of the grain discharged from the silos without shutting down production, as this would save both time and money.
UCML investigated several options for reporting silo grain levels. Load cells, a very accurate method, were too expensive to retrofit onto our existing silos. Repairing our weight and cable system's electronics was also quite costly, considering its mechanical problems. An ideal system would have mechanically and electronically reliable construction, and would be accurate over the full length of the silo—especially the bottom cone discharge section. Such a solution would also have a remote readout capability at some distance from the silo and capability for a high- and low-level alarm shut-off option. Finally, it must be able to handle the grain silo's intense dust level during the filling cycle.
United Canadian Malt was already familiar with Siemens Industry's level measurement transmitters in its manufacturing process. UCML had previously installed a Sitrans LG200 guided wave radar transmitter on a wort tank. Wort is a challenging substance to measure because of high temperatures and excessive steam and foam that are generated during the wort transfer process. The tank also requires a weekly chemical sanitation bath and a high-pressure water washdown, and there is little headroom, complicating the installation of any instrumentation.