What Is the Surge-Trap SPD?
The Surge-Trap is a branded surge protection device (SPD)that utilizes Mersen's patented thermally protected metal oxide varistor (TPMOV) technology. This technology eliminates the need for fuses to be installed in series with the Surge-Trap SPD.
which saves money and panel space. Surge-Trap SPD is typically installed in industrial control panels to protect sensitive electrical equipment from harmful voltage transients. Nearly 80% of all transients are caused by equipment or power disturbances within a facility.
What Types of Ratings Do SPDs Have?
Do SPDs have a current rating? This is a trick question! They do not have a continuous current rating however they do have other important current-based ratings. They are required to have a short circuit current rating (SCCR), which is the maximum rms current at a specified voltage the SPD can withstand.
The nominal discharge current (In) is new to UL 1449 Third Edition (effective 9/29/09). This is the peak value of the current (20kA maximum) through the SPD (8/20μs waveform) where the SPD remains functional after 15 surges.
There are two main voltage ratings for an SPD, the first is maximum continuous operating voltage (MCOV) which is the maximum rms voltage that may be applied to the SPD per each connected mode.
Voltage protection rating (VPR) is determined as the nearest high value (from a list of preferred values) to the measured limiting voltage determined during the transient-voltage surge suppression test using the combination wave generator at a setting of 6kV, 3kA.
How Do I Select The Correct SPD?
Author: Mersen | File Type: PDF
Find more white papers on Control Platforms : Safety Systems