Transient Surges and Surge Suppressor Technologies: Comparing Apples to Oranges
The suppressor to protect a specific point upon an electrical distribution system must be selected accordingly to its physical location.
The sole function of a quality surge suppressor is to protect sensitive electronic equipment from transient overvoltages that are present on AC power circuits. It is irrelevant whether these overvoltages are generated by lightning activity or are induced upon the AC power lines by utility grid switching, power factor correction actions, power cycling of inductive loads, or from other sources. A quality surge suppressor must limit transient overvoltages to values that do not surpass the AC sine wave peak by more than 30% as it initially absorbs intense amounts of transient energy. The suppressor must immediately respond to transients before they reach their uppermost voltage values. Suppressor performance should not deviate or degrade with use when called upon to divert extreme levels of transient current.
Author: WAGO | File Type: PDF